What to know before installation…
First off we must take precautions and understand some basic rules and how electricity works in order to work with it safely. The Canadian electrical code is constantly changing. Every 3 years a new edition comes out in which a committee has gone through and implemented changes and new rules. In addition to the CEC there is also other rules that must be followed, such as local STANDATA’s. These can be variances or changes and additions to the CEC. This is why, especially in commercial or industrial settings, electrical installations are often better left to a master electrician. At CalTrac Services all work is completed by licensed electricians in Calgary and area.
Then there’s the safety and danger aspect of the installation of electrical components. In most instances when installing electrical equipment power is located and disconnected. Ensuring the installation can be accomplished safely without electrical shock. There still ends up being the risk of incorrect wiring. From an intolerable unbalanced load, wrong neutral connection, improper grounding or bonding, and many other code violations.
I could make a book just on all the service calls I have been to that had an extremely dangerous and/or outrageous wiring. One service call from years ago I got called in for a fluorescent light in a kitchen not turning on.
So when I arrived at the house the customer takes me to the light. He tells me that he changed the fixture himself and that it’s not working. Right away assume, “oh, he must of connected a wrong wire, easy fix”. I turn off the switch and go to open the fixture and immediately upon touching the outside of the fixture I get a shocking surprise. A nice electric shock from touching the base of the fixture. So, at this point, I locate the breaker and disconnect the entire circuit. I open the fixture to find a hot wire, not the switch leg, tied directly onto the bonding of the fixture. I of course redo the connections, turn on the circuit and test for proper voltage and function of the light.
That is one of the tamer stories, as I have seen many code violations throughout the years from self installers and fly by nighters. The point is, even if power is turned off and you can accomplish a safe install. In the end when power gets connected to your new circuits there is still risk of improper installation. It could mean arching from poor connections, power on metal enclosures from improper connections, or any number of things. This is why it is extremely important to know the code rules for what you are wiring. As well as have an understanding of how circuitry works. We wont go into the depth of the dangers of electricity here, but there is a lot of information on it. The extreme heat that can be caused from a small arch is more than enough to start a fire.
When your roughin electrical wiring is completed it is time for your inspection. For wiring done in your own home, most municipalities allow for you to obtain a ‘homeowners permit’. If you are having a company work on your home or business, they must obtain their own permit. Be prepared, when you have done the install to know the installation as the inspector will want to go through the what and how. They will confirm that important safety factors and code are in compliance. If there are deficiencies, you will need to correct them and most likely call for a re-inspection.
Below we will go through a general material and tool list. There are several articles out there that give false hope on the extremely low cost and insufficient tool list. Heck I even read one article where it said you could wire your bedroom for 100 bucks. Now I don’t know where they get their wire or electrical devices but I need to find out! Let’s see whats needed for true and a more realistic look at how much money you’ll spend.
Tools and money
For most residential wiring jobs the list below should be sufficient:
- Low Torque corded drill for drilling holes
- 1″ Auger bit (12″ length preferably)
- Holesaw bits (These will be used for recessed lighting, or making larger holes where needed)
- Cordless impact
- Electrical hand tools (screwdrivers – robinson, philips, flathead, etc, strippers, pliers, needlenose, sidecutters, hammer, knife, ect)
- Ladders as required (4 footers are nice for quickly moving around)
- Circuit tester (if you are working on an existing house where you need to find power supplies)
- Cat5 crimps (if you are planning to do your own data)
- Coax stripper and crimps (again if you are planning to do you own data)
- Data tester (cat5 and coax tester for data finishing)
- Electrical meter (don’t get some cheap 20 dollar thing, get something reliable – this is used for confirming voltage, current, and testing ohmic values)
- Work lights (you may need this while you wait for the electrical finishing to happen)
This list for general reference. There maybe more or less tools depending on the job you are trying to accomplish.
Material that will be needed, again is dependent on the job. Here is a list of some of the more common items needed residential electrical.
- 14/2 NMD (used for interior wiring of 15 amp branch circuits and feeders)
- 12/2 NMD (Yellow jacketed) (again interior wiring used for counter plugs and equipment rated for 20 A wiring and breaker)
- 10/3 NMD (used mainly for dryers – 30amp 240V)
- 8/3 NMD (used for ranges – 50Amp 240V)
- 14/3 NMD (this wire is used mainly for 3 and 4 way connections, devices for 120/240V)
- 6/3 wire (Used for larger items such as hottubs – note – if you are going to exterior areas you cannot use NMD but instead TECK90, NMWU, ACWU90, or RW90 depending if you are using a conduit or not)
- Interior wall device boxes (These can range from single gang to 4 gang, octagons for lights, 4 11/16 for ranges or dryers, and others)
- Exterior Plastic device boxes (On exterior walls, in order to keep the vapor barrier seal it is best to now use plastic boxes instead of 2104 with vapor barrier)
- S1 and S2 staples for securing wire
- 4004’s or some type of wire connector
- Fans for bathrooms and Kitchen
- Switches (single poles and 3 ways as required)
- Dimmers (note for 3 ways or LED make sure to buy the proper type)
- Receptacles (many variations and duplex or decora to choose from)
- Light fixtures
- Device cover plates
- Breakers (you will have to know how many archfaults/combination, 15A, 20A, 30A, 2 pulls etc to get)
- Fan interlock relays as required
This not a full list by any means but like mentioned it is some more of the common items that will be needed for your residential venture.
Safety and code
Circuit capacity refers to the maximum amount of current or devices that you can place on a circuit. A circuit is a loop of the devices on breaker or overcurrent device. In residential most circuits are 15 amps.
For general use receptacles you are allowed 12 devices (refer to 8-304 CEC rule). Most other common household circuits it is rated at 80% overcurrent capacity. So for a 15A circuit we can go 120V x 15A x 80% which equals 1440 watts or 12 Amps. More information on capacity of circuits can be found in section 8 and section 14 of CEC.
For information on electrical wiring methods see section 12 and section 26. In section 26-700 – 714 it talks about receptacles and placement and requirments. Such as wall space between receptacles and countertop spacing between receptacles. All these sections should be understood in order to properly wire, even for simple installs.
Calculations of residential services and total ampacity required can be done through section 8 of CEC. This can become very complicated and is best left to a professional. For example if your adding a legal suite you may be required to do a full calculation. If the calculations end up at certain point you may even need to upgrade your service to a 200Amp. This is a part that can be slipped by and I have seen it happen. It is best to be prepared for it. So if you are adding a lot of power you maybe best to get a licensed electrician to do these calculations for you.
Tamper resistant receptacles
If we look again at section 26 of the CEC we will find that many of the receptacles in a residential home are to be tamper resistant. This is maily for protection against someone, especially children getting electrocuted. For exemptions for tamper proof see rule 26-700 and 712. In general it is a good idea to just install TR receptacles throughout as it wont hurt anything.
Archfault and GFI circuits
As we looked at above in section 26 of the CEC we can see it gives information on the requirments of archfaults and GFCI circuits/receptacles. For example any receptacle within 1.5 of a sink, basin, tub shall be protected by a GFCI device.
If we move to section 30 in CEC we can also see that a switch within 1000mm to 500mm will be required to be GFI protected. Section 26-720 explains a bit as well for combination archfault devices. Most circuits that have an outlet installed will require a combination archfault.
For exemptions on circuits not requiring archfault protection go through section 26. A side not, if you have a older panel, for example a federal stablock it does not have a combination archfault available. You would actually need to run a deadfront combination archfault in order to achieve proper protection. It is good to note that the CEC can become daunting and confusing, especially if you have never gone to school. For example you would have to go to section 62 to find out you would need GFI protection for heating devices near sinks or showers. This is a good reason why there is 4 years in Alberta apprenticeship and another 3 years before you can obtain you Masters. The electrical trade is filled with many rules and is constantly changing code and safety implementations.
Roughing in electrical
Some quick tips:
- Keep track of the homeruns (wire pulls from a device to the panel) you pull back to the panel and if they have a outlet on that circuit. This circuit will require an archfault most likely (again depends on the exemptions). It can be a pain to try and find all the circuits that require an archfault at the end and nothing is marked.
- Try to keep your lighting and outlet circuits separated.
- On roughin finish all your connections in your boxes. If there needs to be pigtails or connections made, do them now (don’t be lazy). Because when you come back on finishing and can’t remember you’ll be going around toning and doing continuity test to find wires. I even strip the ends of the wires, this way on finishing you don’t have a bunch of ends to pick up off the floor.
- REMEMBER – 2018 code is here, and it has a a whole wack of changes, additions and deletions. One in particular is with switching. Each switch must have its neutral brought to the device box as well. This means no more 2 wire switch legs.
- When tying wire into a switch box be sure to mark the wires. For example notch the wires that are switch legs from the light. And mark which wires go together. Which travellers go with which wire. I tend to twist the wires that go together with each other and roll them into the box
- Make sure you push your wires back in the electrical box. When it comes time for drywall you don’t want drywaller to end up cutting your wire in the box.
- With the above point in mid, always add a loop at each box. This is even a code rule.
For potlight or recessed lighting the days of installing a recessed lighting box are becoming less and less. You see before if you wanted a recessed light you would first install a can either ICF or non-ICF depending whether there was insulation and the manufactures rating.
Then on finishing you would install the trim and light bulb. Not to say that these types of fixture don’t have there place. But now with technology comes change. You can now purchase LED lights the depth of half an inch. This suggest they can be installed in many places where shallow depth are required. If you are doing new construction it is a good idea to get the metal templates for the LED lighting. This way when drywall goes on the drywallers will know exactly where to cutout each hole. Also in addition to the benefits listed these lights are LED and therefore draw far less power and can upto 20 years.
For circuit capacity we can see that with a 9w light we can put many of these lights on the same circuit. Compare that to a 100W fixture and you can see the difference.
Kitchen outlets are to be either 20A devices or split receptacles. Nowadays it is more common to run 12/2 and install 20 amp devices. More and more applainces draw more power and it is less complicated to install. For example if you require a GFCI on a counter it is far cheaper to purchase a 20 A GFI than a 2 pole GFCI breaker. Any counter space more than 300mm will require a outlet and there shall be no more than 900mm without an outlet. Also note, there cannot be an outlet directly behind the sink area. See section 26-712 for more info.
Building and electrical code require smoke/carbon detectors. See section 32-110 for some information on electrical aspect. For instance interlocking of all the smoke detectors is a requirement. We can accomplish this by using a 14/3 cable between each detector. It also requires the detectors to be feed from a circuit that has lighting on it. Usually done by connecting to the hall lighting circuit. One reason is if the lights go out we’ll fix them or rather know that they need to be fixed. Where if it was an outlet or by themselves it may end up going unnoticed.
Also new code requires for detectors to be installed and interconnected in more locations in a dwelling unit. In each bedroom you are required to have a smoke detector as well.
Building code and plastic boxes
New building code has come into effect, essentially making metal boxes with vapor barriers obsolete. This is due to the type of air tight seal required in new homes. It is far more efficient to use plastic boxes with foam seal on the connections in new installations. These will be required on any exterior wall including the attic area.
Exterior lighting and wiring
During roughin stage any lighting or devices required outside need to be completed. Trust me you dont want to be trying to fish new lines that were forgot through brand new painted drywall. So if you are going to require circuits for say lighting post, soffit plugs, irrigation, or AC now is the time to run them. Keep in mind that exterior wiring is different than interior. For instance if you are burying wire you will need to use a wire that is rated for underground or exterior use. One of the more common ways is to run PVC (pipe) from the side of the house underground and come up to the location needed. Keep in mind mechanical protection for the wiring, seal connections, proper bonding of equipment.
3 or 4 way
For wiring a 3 way or 4 way can be a tricky thing for a novice or even apprentices to learn. With a 3 way you will need 2 travelers between the 2 switches. Then at one end you will have a constant hot and the other you will have the switch leg (A black/red wire going to the light for switching on and off). So however you make this happen is fine. So one switch will have 2 travelers and a hot and the other will have 2 travelers and a switch leg. For a 4 way you just continue the travelers from switch to switch to switch and on and on and on to nth way. Inside the 4 way you will have 4 wires, 2 travelers from the first switch and 2 travelers from the last switch. To get a better idea look at the diagram below.
Hot tub or spa
Lots of people have a hottub. I do and I know I love it, and so do the people that come over. Most people know that water (I should say non distilled) and electricity don’t mix well. Then add people in the mix and that’s just dangerous. So if your are planning to wire a hot tub it is best to hire a professional and someone who knows the code rules and reasons for them. First the you will have to find a way to get your wire to the outside location. Once there you will need to install a disconnect or more commonly call a spa pack. This includes a GFCI rated at your hottubs manufactured rating. Common sizes are 40, 50, and 60 Amp.
Also note most hottubs require copper wiring, so its a good idea not to cheap out and buy aluminum here. Ensure all components are rated for the ampacity of the hottub. If you look on the nameplate of the hottub you can see the manufacture requirements. It usually even tells you the size of the cable required and size of the overcurrent device.
Service and panel installation
For brand new homes a meter, panel, and service wiring needs to be installed. Most municipalities require for a ticketed contractor with a business license to install these. As well this is something that is best left to a licensed electrical company. Here at CalTrac we would be happy to assist you with electrical work.
These rules are mainly found in section 6 and for dwelling units table 38 can be used to find correct overcurrent and conductor sizing. Although there is many other references throughout the code book including the Alberta Standata.
For new homes the utility company will sometimes leave the wire buried or else you will need to run the wire. This is something to find out. Also you will need an inspection done and a site id in order for the utility company to connect power.
In simple terms the process is as follows. Most utility companies, such as enmax and fortis have their own guidelines and set of rules for installers and electricians to follow when constructing a service. For residential, there is certain areas that can be cold or hot sequences. For this example we will use hot sequence as it’s more common in residential. This means there is no disconnection means before the customers meter or supply portion.
Most new services are underground and most old or re-done services are overhead. A meterbase is mounted on the side of the house at a specific height. This is then ran, usaully with pipe such as PVC to the inside. Note here, there are code rules to follow and understand, such as the maximum distance you can run on the inside of a dwelling unit. Once the wire is in the inside of the building it is connected to the panel. There is also the connection of the grounding and bonding of metallic enclosures. This a simple run down of the procedure and is not meant as a toturial for connecting a service or utility wire. You will need a professional to install this portion as it is extremely important to get right. More information on services can be found at this article Panel Upgrading and Service Upgrading.
Also with 2018 CEC there is new code rules to follow. Such as grounding of systems starts on the supply side. Meaning the identified/grounding conductor must be on isolated lugs in the meterbase. On a system there should be only one point that is grounded. It can now be in the meterbase or panel. Care has to be taken that any jumpers are removed, such as a jumper screw in the main panel. As a side note, when installing a subpanel, it should be noted that the jumper should be removed in this panel as well. This would still be part of the same system and therefore is only bonded.
Wiring for smarthome
There are more and more products and companies coming onto the market now for smarthome functionalities. The one you choose is simply dependent on what your needs are. For instance on one home we wired we wanted everything to be able to be controlled from Google home. The multiroom speakers, lights, irrigation, thermostat, doorbell, and locks. For smarthomes it’s a good idea to keep in mid to be able to control devices from your phone or computer you need a hub. Some common manufactures are insteon, lutron, z-wave, etc. For the following we will use
Insteon as an example. The reason being is because they offer alot of products and diversity.
For the most part you roughin electrical the exact same way as tradional electrical. Most smart switches will require a hot, neutral, and the switch leg from the light. As per new CEC of 2018 all switches require a neutral now anyways so this shouldn’t be a worry. The one difference is when you wire 3 or 4 ways with smart switches. The 2 travellers are not needed and end up being capped off or used to get power to the other switch.
Note that you should always roughin your home as per standard electrical. This will ensure you can always use normal or non-smarthome switches and devices if wanted. For example if you plan on selling or changing you home down the road.
For irrigation connecting into your smarthome ther are a few options. The one we have used most is b-hyve. This is because it works by voice control through google home.
There are many options to choose from when it comes to thermstats. For smarthome intergration they, for the most part do the same thing. You are able to connect through an appand control from remote locations. They can get local weather and control through automated schedules. The wiring for smart thermostats is the same except you will have to make sure you have a ‘C’ wire. A c wire or ‘common’ wire is a wire that comes from your furnace and sends a constant 24 volts. Most wifi thermostats require it for power. So when your doing your roughin make sure to run enough wires to have a c wire as well. It’s a good idea to run at least a 6 conductor anyway for future use.
Doorbell and locks
For doorbells you will won’t need to change any of the wiring. Just run you 18/2 from the front to the doorbell and another 18/2 from the doorbell to the downstairs panel area for power. Take a look at the common wiring for most residential doorbell systems. Note that most units, such as the ring, require you to recharge them via a cable. As for doorlocks and intergrating them, there is no requirment for the wiring. They are powered by battery power.
Smarthome integration of Multi room speakers
Multiroom speakers are an amazing feature to have. Here we will only discuss the intergration of google home and multiroom speakers. This feature can become extermely expensive, into the 10’s of thousands. As tradiontally you would have an amp and run wall plates/selectors and ceiling speakers. But with technology coes many changes and this time for the better.
There is a couple ways you can do this, the way I prefer is using ceiling speakers and a multiroom amplifier. The idea is to hook up chromecast audio devices to each speaker. These can be bookshelf speakers or you can run wire for ceiling speakers. If you run ceiling speakers you will need a central multi room amp with RCA inputs for individual pairs of speakers. Because Google chromecast audios can be grouped and indivually selected, you can play different audio in different locations. Also because it’s Google you can use voice commands. Such as “Hey Google, play rock playlist in Mast bedroom” and poof you got music going.
Sensore are devices that can let you know of open or close, or water leaks, or day or night, or motion detected. For the most part these are becoming more and more wifi for residential/homeowner use. They are not mean to be a true alarm system but more so a indicator for you personal use. For example you can remember if you shut the garage door, well look on your phone app. Or you upstairs washer is leaking, you will be notified of the presence on water from your phone.
Most sensors require a hub and batteries to operate. For instance the Insteon light switches and sensors can use the same hub. You will know whenyou door is opened, a light turns on, or motion is detected. As for wiring, because most manufactures are based on wifi there is no wiring needed.
Inspection of installation
Once your roughin of electrical is completed you will be requred to have an inspection. Because this is wiring done by yourself it will require a homeowners permit. For more information just call your city for information. There will be 2 parts to most electrical inspections. A roughin and a final. A roughin inspection is important to complete not just for the safety and complainace aspects. But for the fact that if electrical work was done without one you can be required to take down finished drywall. You can also end up being fined. I can’t tell you how many times I have been asked to come in and verify electrical that was never inspected. It can become a big bill in the end.
Finishing electrical and connecting power
Once your walls are finished your ready to connect devices. First go around and count how many of each devices are need and how many wall plates. Count the amount of breakers required if they are not completed. Keep in mind the arch faults required. These are required where you have receptacles being feed from a circuit, excluding any exemptions. Once all devices are on you can begin to power up your system.
Here go around one more time and confirm all JB’s, receptacles, switches, and any other electrical connections are complete. Once confirmed and confident you can start to turn your circuits on one by one. If nothing trips then most likely your on the way for completion. But if somethings happens to short out and trip the break you’ll have an issue to resolve.
These issues can be from nails or drywall screws puncturing the wire to doing an incorrect splice somewhere. You will need to find out the circuit that is tripping and what it feeds. Find the first device and (with the power off) test for continuity between hot and nutrient. If you have a continuity it is hopefully a bad connection somewhere. You can start with the first device work your way down until you find the issue. We won’t go into too much detail on troubleshooting here but perhaps in a later article.
Once all the circuits are on go around with a plug tester and test each plug and test all your switches. If everything is working and proper voltage and correct polarity than now is the time to mark your panelboard. This is easier with 2 people as one can flip the breakers and one can go around with a tester. You have to mark every circuit breaker you have, so make sure this is done accurately.
So in conclusion we can see there is an abundance of rules to follow, even when it comes to a simple residential installation. If your not confident in your ability it is always a good idea to hire a licensed professional. We all like to save money but sometimes it is better to leave it to someone with years of experience. If you do happen to hire someone make sure to hire someone who is ticketed and licensed. The last thing you want is to save a few bucks to hire joe blow and he can’t even get a permit or forgets lines to connect. We have seen it all to often when someone calls and needs to troubleshoot an entire house or is requesting for a concealed permit because they never got one.
In the end if you do complete the work yourself, just follow the rules, go slow, and get an inspection done. If it seems like something you like to have a professional electrical company take a look don’t hesitate to give us a call at 403-651-2621. We take extreme pride in our work and love what we do and if you need help with a project we would love advise and work with you. We serve Calgary and area with high quality and satisfaction guaranteed. CalTrac – Calgary Electrical Company.